Hv ABC Cable, Aerial Bundled Cable, Al/XLPE/Cws/HDPE+Gsw, 3/C+1/C, 12.7/22 Kv (AS/NZS 3599.1)
|FOB Price:||US $1-25 / Meter|
|Min. Order:||500 Meters|
|Min. Order||FOB Price|
|500 Meters||US $1-25/ Meter|
|Production Capacity:||12000 Km/Year|
|Transport Package:||Fumigated Steel-Wooden Drum/Steel Drum|
|Payment Terms:||L/C, T/T, D/P, Paypal, Western Union|
- Model NO.: Hv ABC Cable
- Conductor Type: Stranded
- Conductor Material: Aluminum
- Insulation Material: XLPE
- Range of Application: Distribution
- Brand: Boan
- Rated Voltage: 12.7/22 Kv
- Size: 35-185 mm2
- Type of Screen: Copper Wire Screen
- Trademark: DingAn
- Origin: Jiangsu Yixing, China
- Type: Insulated
- Application: Overhead
- Sheath Material: HDPE
- Material Shape: Round Wire
- Certification: ISO9001, CCC
- Manufacture Standard: AS/NZS 3599.1
- Number of Cores: 3+1
- Class of Conductor: 2
- Type of Support Conductor: Gsw
- Specification: SGS
- HS Code: 8544601200
Metallic Screened HV ABC
Phase conductors are stranded circular compacted aluminium alloy 1350 to H68 condition. The standard catenary is manufactured from galvanised stranded high tensile steel. For corrosive environments catenaries of aluminium clad steel are available.
Conductor Screen, Insulation and Insulation Screen
Semiconductive conductor screen, XLPE insulation and semiconductive insulation screen are triple extruded. The insulation screen is hand strippable without preheating and complies with strippability and adhesion tests given in AS/NZS 3599.1. Figures and words "1 ONE," "2 TWO" and "3 THREE" are printed on the insulation screen to identify the three phase cores. Alternative identification means are available on request.
A water swellable textile tape is applied over the insulation screen to prevent longitudinal ingress of moisture in the event of damage to the outer sheath.
The metallic screen comprises a layer of helically applied copper wires. For short circuit protection, two types of screens, a light and a heavy duty, are available. A separator tape to prevent the penetration of sheath material between the screen wires is applied over the metallic screen. On this design of cable it should be noted that the screens of individual cores are not in direct contact with each other and therefore the fault current level is limited.
High density polyethylene (HDPE) is used as the standard outer sheath of each phase core. In addition to the identification on the cores, the sheaths of each phase cable are marked with phase numbers matching those of the cores.
The cable bundle
The three single core cables are bundled around the galvanised steel catenary in a right hand lay.
(a) Normal operation 90°C
(b) Emergency operation 105°C
(c) Short circuit operation 250°C (5s max)
This cable can be used for aerial as well as underground installations.
|HV XLPE Insulated Metallic Screend ABC 6.35/11 KV|
|Nominal Conductor Area||Average Insulation Thickness||Average Insulation Screen Thickness||Copper Wire Screen Thickness||Galvanised Steel Catenary stranding||Nominal Overall Diameter||Approx. Mass||DC Resistance at 20°C|
|Galvanised Steel Catenaries|
|Stranding & Nom. Wire Dia.||no/mm||7/2.00||19/2.00|
|Nominal Overall Diameter||mm||6.0||10.0|
|DC Resistance at 20°C||Ω/km||8.7||3.2|
|Minimum Breaking Load||kN||26.0||70.5|